Preventing wet stacking
Prevention of wet stacking drives many of the details of generator testing requirements.
Generally, any mention of wet stacking generates a lot of questions. Wet stacking is a phenomenon that affects diesel engines—on the steel side of the unit. Articles like this are read by people with electrical expertise—on the copper side. Prevention of wet stacking drives many of the details of generator testing requirements, so a brief description is presented here.
When a diesel engine runs at light load, its fuel rate is low, and it doesn’t generate much heat with each power stroke. The cylinder walls stay relatively cool and don’t support complete fuel combustion. The unburned fuel exits the cylinder as vapor and carbon particles. Vapor condenses in the exhaust system,and appears as a thick black liquid at the system exit ports-typically, the engine exhaust outlets and the turbocharger. Historically, the exhaust outlets were called "stacks." When liquid appears at the stack outlets, the engine is said to be "wet stacking."
Figure 4 shows a 1,000 kW diesel generator in this condition. Unburned liquid fuel mixed with carbon particles result in a gooey mess, and drip from the stacks and from the turbocharger. The liquid tends to run along the joints in the engine. The appearance is a bit frightening; it looks like every seal in the engine has sprung a leak. In its early stages, though, wet stacking isn’t particularly serious. The cure is to run the engine at reasonable loads for an extended period, using a load bank or available building load, to evaporate the liquid and blow the soot out of the exhaust system.
Extended periods of operation at light load can have serious and expensive consequences. Piston rings don’t scrape away the oil film on the cylinder walls, and the remaining oil above the rings is exposed to high combustion temperatures. Under those conditions, the residual oil forms a hard, nonuniform film,disrupting the close mating between the rings and the cylinder wall. Fuel can slip past the rings to contaminate the oil, and the gaps in the film can result in a loss of compression. The piston rings can no longer support the high pressures of the power stroke, and the engine can no longer develop its maximum output power. This phenomenon is called "cylinder wall glazing," and when it’s severe, it can’t be resolved with a high-load run. Severe glazing requires an engine rebuild, with re-honing of the cylinders or liners, to restore engine performance.
Repetitive operation at light loads results in unwarranted confidence in the generators, in that they continually pass tests but often can’t deliver adequate power to their connected loads when the utility fails.
Tom Divine is a senior electrical engineer and project manager at Smith Seckman Reid Inc. He is a frequent contributor to Consulting-Specifying Engineer magazine and Pure Power, and is often a speaker at CSE Webcasts.