# Generator sizing examples

## When designing generator systems, such as engine-driven generator sets, design engineers must ensure that the generator selection, sizing, and the design of electrical systems are appropriate for the application.

03/14/2016

Consider the task of sizing a 277/480 V, 3-phase generator for three different loading and motor-starting methods. All three examples use the following loads:

• One 150-hp motor, Code F, 95% running efficiency, 0.26 starting PF, and 0.86 running PF
• One 200-hp motor, Code G, 95.4% running efficiency, 0.24 starting PF, and 0.87 running PF
• Miscellaneous loads of 75 kVA, 0.84 starting PF, and 0.91 running PF.

Motor load: The following equations are used to calculate SkVA, SkW, RkVA, and RkW:

SkVA = motor hp x locked-rotor kVA/hp

Where locked-rotor, Code F motor = 5.5 kVA/hp; Code G motor = 6 kVA/hp per NEC, Table 430.7(B)

SkW = SkVA x starting motor PF

RkW = motor hp x 0.746-kW/hp/efficiency

RkVA = RkW/running motor PF

Miscellaneous load: The following equations are used to calculate SkW and RkW:

SkW = SkVA x starting PF

RkW = RkVA x starting PF

Where load kVA remains constant: kVA = SkVA = RkVA

Example 1: A 1,000-kW generator with 2,525 SkVA at 20% voltage dip is selected from the manufacturer's specification sheet to supply a total load of 2,100 SkVA. The total load of 342 RkW is 34% of the 1,000-kW generator rating. The generator is under-loaded in the final running condition because of the required oversized generator capacity to meet the starting kVA.

Example 2: An 800-kW generator with 2,000 SkVA at 20% voltage dip is selected from the manufacturer's specification sheet to supply a total load of 1,412 SkVA. The total load of 342 RkW is 43% of the 800-kW generator rating. The generator is under-loaded in the final running condition because of the required oversized generator capacity to meet the starting kVA. When loads were stagger-started (step-loading), the generator SkVA was reduced from the SkVA required in the example of starting all loads concurrently.

Example 3: A 400-kW generator with 765 SkVA at 20% voltage dip is selected from the manufacturer's specification sheet to supply a total load of 710 SkVA. The total load of 342 RkW is 86% of the 400-kW generator rating. The generator is loaded to around 86% of its rating in the final running condition, assuming transients are acceptable. When loads were stagger-started and reduced voltage was used to start motor loads, the required generator SkVA was significantly reduced.

Tarek Tousson is senior electrical engineer at Stanley Consultants. His expertise is motors, generators, and UPS systems, and he has 20 years of experience designing electrical power distribution systems for mission critical facilities and other types of buildings.

References

NFPA 110: Standard for Emergency and Standby Power Systems covers

Consulting-Specifying Engineer's Product of the Year (POY) contest is the premier award for new products in the HVAC, fire, electrical, and...
Consulting-Specifying Engineer magazine is dedicated to encouraging and recognizing the most talented young individuals...
The MEP Giants program lists the top mechanical, electrical, plumbing, and fire protection engineering firms in the United States.
Emergency power requirements, salary survey results, lighting controls, fire pumps, healthcare facilities, and more
Approaches to building engineering, 2018 Commissioning Giants, integrated project delivery, improving construction efficiency, an IPD primer, collaborative projects, NFPA 13 sprinkler systems.
Power boiler control, Product of the Year, power generation,and integration and interoperability
This course focuses on climate analysis, appropriateness of cooling system selection, and combining cooling systems.
This course will help identify and reveal electrical hazards and identify the solutions to implementing and maintaining a safe work environment.
This course explains how maintaining power and communication systems through emergency power-generation systems is critical.
Data centers, data closets, edge and cloud computing, co-location facilities, and similar topics are among the fastest-changing in the industry.