# Distribution vs. Transmission: Comparing Tariffs

## Larger industrial and commercial building owners can restructure their electric service to best take advantage of the deregulated environment. The end-user can select a preferred generation source, and, in effect, use the electric transmission system as a common carrier to get energy to his facility, bypassing altogether the local utility's distribution system.

11/01/2000

Larger industrial and commercial building owners can restructure their electric service to best take advantage of the deregulated environment. The end-user can select a preferred generation source, and, in effect, use the electric transmission system as a common carrier to get energy to his facility, bypassing altogether the local utility's distribution system.

The decision to bypass the distribution system is primarily economic. Transmission service is generally much less expensive, and having choice implies competition on price.

However, to have access to the interconnected utility grid and multiple generation providers, the end-user's electric service must migrate from the serving utility's distribution system to the transmission system. Also, the industrial facility must assume all of the design and operational responsibilities traditionally handled by the utility.

To assist in determining whether the additional work is worth the savings, it helps to quantify them. The attached tables, which compare the distribution and transmission tariffs from a large Midwestern utility, show a typical industrial load using both tariffs, as well as the percentage savings for sample load ranges and load factors.

Table 1 - Typical Tariffs and Industrial Load Calculations

TYPICAL TARIFFSDistribution serviceTransmission service

Service charge

\$10.00

\$100.00

Demand charge

First 1,000 kW: 12.11 per kW

First 50,000 kVA: 10.53 per kVA

Energy charge

Demand times 300: 0.01905 per kWh

Demand times 300: 0.0085 per kWh

INDUSTRIAL EXAMPLE

Distribution service

Transmission service

Service charge

\$10.00

\$100.00

Demand charge

1,000 kW X \$12.11 = \$12,110.00

3,500 kW X \$10.53 = \$368,550.00

34,000 kW X\$10.51 = \$357,340.00

Energy charge

35,000 X 300 = 10,500,000 X 0.01905 = \$200,025.00

35,000 X 300 = 10,500,000 X 0.0085 = \$89,250.00

(17,885,000-10,500,000) X \$0.0072 = \$53,172.00

(17,885,000-10,500,000) X \$0.0067 = \$49,479.00

Total

\$622,657

\$507,379

Transmission tariffs from a large Midwestern utility show that they are generally much cheaper than distribution rates. An industrial facility with a 35,000-kW load and a monthly energy consumption of 17,885,000 kWh-and a load factor of 70 percent-will have the charges shown above (fuel charge excluded) at 100-percent power factor.

Table 2 - Savings

10,000

19.0

20,000

18.7

30,000

18.5

40,000

18.5

50,000

18.5

60,000

18.4

70,000

18.4

80,000

18.4

90,000

18.4

100,000

18.4

Using the tariffs shown in Table 1, potential savings were calculated over a broad range of demands, showing a consistent level of savings. Another major variable to consider is load factor, which is found by dividing the total annual energy consumed by the demand, multiplied by 8,760 hours per year. The lower values shown represent peak loads.

0.5

19.2

0.55

19.1

0.6

18.9

0.65

18.7

0.7

18.5

0.75

18.3

0.8

18.2

0.85

18.0

0.9

17.9

0.95

17.7

1

17.6

Consulting-Specifying Engineer's Product of the Year (POY) contest is the premier award for new products in the HVAC, fire, electrical, and...
Consulting-Specifying Engineer magazine is dedicated to encouraging and recognizing the most talented young individuals...
The MEP Giants program lists the top mechanical, electrical, plumbing, and fire protection engineering firms in the United States.
How to use IPD; 2017 Commissioning Giants; CFDs and harmonic mitigation; Eight steps to determine plumbing system requirements
2017 MEP Giants; Mergers and acquisitions report; ASHRAE 62.1; LEED v4 updates and tips; Understanding overcurrent protection
Integrating electrical and HVAC for energy efficiency; Mixed-use buildings; ASHRAE 90.4; Wireless fire alarms assessment and challenges
Power system design for high-performance buildings; mitigating arc flash hazards
Transformers; Electrical system design; Selecting and sizing transformers; Grounded and ungrounded system design, Paralleling generator systems
Commissioning electrical systems; Designing emergency and standby generator systems; VFDs in high-performance buildings
As brand protection manager for Eatonâ€™s Electrical Sector, Tom Grace oversees counterfeit awareness...
Amara Rozgus is chief editor and content manager of Consulting-Specifier Engineer magazine.
IEEE power industry experts bring their combined experience in the electrical power industry...
Michael Heinsdorf, P.E., LEED AP, CDT is an Engineering Specification Writer at ARCOM MasterSpec.
Automation Engineer; Wood Group
System Integrator; Cross Integrated Systems Group
Fire & Life Safety Engineer; Technip USA Inc.
This course focuses on climate analysis, appropriateness of cooling system selection, and combining cooling systems.
This course will help identify and reveal electrical hazards and identify the solutions to implementing and maintaining a safe work environment.
This course explains how maintaining power and communication systems through emergency power-generation systems is critical.