# ASHRAE 62.1: uncommon calculations, approaches

## ASHRAE Standard 62.1 is best known for its regulation of the amount of ventilation air delivered to each space by HVAC systems through its ventilation-rate procedure approach to system design. ASHRAE 62.1 offers many calculations and performance approaches.

**Learning objectives:**

- Know the basics of ASHRAE Standard 62.1: Ventilation for Acceptable Indoor Air Quality.
- Summarize the less common calculations within this standard.
- Review examples to enhance the understanding of these calculations.

Most HVAC engineers are familiar with ASHRAE Standard 62.1: Ventilation for Acceptable Indoor Air Quality. Likewise, the fundamental calculations required by the standard are also generally familiar and have been adopted into many building codes within the United States, either explicitly or as an alternative means of compliance.

However, there are some calculations that are less commonly applied and/or codified that are worth exploring. Some of these calculations are required when pursuing green building certifications, such as U.S. Green Building Council LEED compliance, as a part of the overall ASHRAE 62.1 compliance documentation (though some are often ignored by many practitioners and reviewers). Other calculations can help the designer improve the ventilation and indoor-air quality (IAQ) performance of their designs or offer performance-based alternatives to prescriptive requirements for consideration.

While this article offers an overview of some of these calculations, users of the standard are encouraged to purchase the ASHRAE 62.1-2016 User's Manual and accompanying calculation spreadsheets from ASHRAE for a thorough and complete understanding of all aspects of the standard.

This article will summarize and provide examples for the following less common calculations included within ASHRAE Standard 62.1-2016:

- Section 5.9.1: Relative Humidity (RH).
- Section 6.2.6.2: Short-Term Conditions.
- Appendix A, A1.2.2: Secondary Recirculation Air Systems.
- Appendix B, B2: Determining L Distance (for exhaust-air outlet separations).

**Section 5.9.1: Relative Humidity **

Section 5 is an important portion of the standard that many engineers and architects often fail to fully evaluate for compliance. This section of the standard governs many aspects of the HVAC and building (read: architectural) systems that impact IAQ. Aspects governed by this section include duct and air distribution system design, air handling system design, outside-air intake proximity to exhausts and other potential contaminant sources, controls, filtration, rain entrainment and façade moisture management, and operations and maintenance, to name just some of the many important aspects covered by the standard and required for compliance.

One important, and often overlooked, aspect of good ventilation and HVAC system design is the control of indoor RH. While the standard does not attempt to mandate design checks for all system operational situations, Section 5.9.1 requires the designer to address RH management of the HVAC system under a typical dehumidification design condition.

The dehumidification design condition within the standard is to maintain a maximum indoor RH of 65% under the following:

- Outdoor conditions at the dehumidification design conditions (user-stipulated at the 2%, 1%, or 0.4% conditions); dewpoint and mean coincident dry-bulb temperatures.
- Indoor sensible and latent loads at design conditions.
- No solar loads (but shall include envelope conduction and infiltration loads).

It is important to consider this type of scenario, as well as other part-load scenarios with potentially high outdoor or indoor latent loads, when designing HVAC systems to properly manage indoor RH, especially in warm and humid climate zones that predominate in the eastern and southern United States.

**Relative humidity: Example 1**

- Location: Baltimore.
- 1% design conditions: 74.1°F dew point; 81.1°F mean coincident dry-bulb temperatures.
- Indoor design target: 74°F dry-bulb; 65% RH.
- Space: A 1,000-sq-ft conference room with an exterior window.
- System type: Variable air volume (VAV).
- Internal loads: 17,000 Btu/h sensible; 10,000 Btu/h latent.
- Envelope load (conduction): 500 Btu/h sensible.
- Infiltration load: 300 Btu/h sensible; 1,200 Btu/h latent.
- Total space load: 17,800 Btu/h sensible; 11,200 Btu/hour latent; sensible heat ratio (SHR) = 0.61.

For the analysis, we will assume that the system is a VAV system with a typical supply air condition of 55°F dry-bulb, 54°F wet-bulb under the aforementioned design condition, with the supply airflow rate determined by the space-sensible cooling load. This results in a delivered airflow rate of 825 cfm.

The resulting psychrometric analysis shows that the indoor space conditions will be 74°F dry-bulb, 63% RH (see Figure 1). In this condition, the HVAC system design meets the ASHRAE design requirements as outlined in Section 5.9.1 of the standard. However, the designer should note that the conditions are very close to the maximum allowed—any adjustments in supply air temperature above the design condition should be avoided to maintain acceptable indoor RH conditions.

**Relative humidity: Example 2**

- Location: Los Angeles.
- 1% design conditions: 66.2°F dew point; 73°F mean coincident dry-bulb temperatures.
- Indoor design target: 74°F dry-bulb; 65% RH.
- Space: A 500-sqft cocktail lounge with two exterior windows.
- System type: Dedicated outside-air system (DOAS) with chilled-water fan coil unit (FCU).
- Internal loads: 17,250 Btu/h sensible; 13,750 Btu/h latent.
- Envelope load (conduction): -200 Btu/h sensible.
- Infiltration load: -50 Btu/h sensible; 525 Btu/h latent.
- Total space load: 17,000 Btu/h sensible; 14,275 Btu/h latent; SHR = 0.54.
- Peak-cooling space-sensible load: 25,000 Btu/h, including solar load (for FCU system sizing).

For the analysis, we will assume that the DOAS provides ventilation air at a constant rate of 450 cfm at a supply air condition of 55°F dry-bulb, 54°F wet-bulb. We will assume that the fan coil runs at a constant volume of 750 cfm and modulates its cooling coil to meet the space's dry-bulb setpoint. The ventilation air provides 9,720 Btu/h of sensible cooling, with the fan coil picking up the remaining 7,280 Btu/h of sensible cooling at a supply air condition of 65°F dry-bulb, 62.7°F wet-bulb (sensible-only cooling is assumed due to the part-load operation).

With an SHR of 0.54, the resultant predicted indoor RH is 72%. This clearly fails the required design criteria (see Figure 2). In reality, the indoor RH will be higher than 72%, as the initial analysis assumed a drier starting point for the FCU cooling coil, which will result in a higher-enthalpy mixed-air condition and resultant higher indoor RH.

In this condition, the designer must modify the design or controls to meet the required maximum RH of 65%. The conventional, if inefficient, approach would be to subcool and reheat at the FCU to meet the RH target. The more energy-efficient approach would be to use a variable-speed (not multispeed/staged fan control) fan coil and maintain a constant supply air temperature off the fan coil of approximately 55°F. This would provide additional latent cooling without wasteful reheat energy consumption.

** Short-term conditions**

Section 6.2.6.2, Short-Term Conditions, addresses design situations that occur less frequently, but are helpful to give the designer flexibility in designing a right-sized ventilation system. Some space types, projects, or program areas have highly intermittent occupancies, which may not warrant the full ventilation flow rate on a constant basis that would otherwise be determined by the standard if occupancy were relatively constant.

The standard approaches averaging by looking at an averaging time that is equivalent to three time constants (approximately 95%) of the space without any averaging reductions. The formula is given as Equation 6.2.6.2-1 (IP):

Where

v = the volume of the ventilation zone, in ft^{3}.

V_{bz} = the breathing zone outside airflow rate, in cubic feet per minute, calculated per equation 6.2.2.1 at the design, steady-state, population.

T = averaging time (minutes).

Once the time period is calculated, the variable occupancy can be averaged over that period. In addition to allowing the ventilation rate to be based on an average occupancy over that time period, the standard also allows the designer to vary the supply of ventilation air to the space over time, provided the time-averaged ventilation rate is met.

For example, the ventilation supply could be varied by cycling a VAV box damper between closed and open positions or cycling an outside-air damper for a system. Averaging the ventilation supply can be helpful in meeting low-ventilation requirements in equipment with insufficient turndown.

**Variable-occupancy example **

Setting: A 10,000-sq-ft concert hall lobby with 43.5-ft ceilings. The lobby is expected to hold a maximum of 1,500 guests ahead of the concert, with guests expected to arrive over the course of 1 hour, all mingling for 15 minutes before the main hall doors are opened and then entering the hall over the course of another 15 minutes. The lobby remains empty for 2 hours during the concert. The guests then exit over 15 minutes, and the venue is then empty for the remainder of the night (staff ignored for simplicity). This occupancy profile is shown in Figure 3.

The first step is to determine the time period over which the averaging must occur. The space volume is 435,000 ft^{3}. The breathing-zone ventilation rate, assuming a zone-ventilation effectiveness of 1.0, is calculated based on the peak occupancy of 1,500 people and an area of 10,000 sq ft = 1,500 x 2.5 + 10,000 x 0.06 = 4,350 cfm. Therefore:

The average occupancy over the course of the 5-hour time-averaging period is, therefore, 337.5 occupants. This revised average occupancy can be used to calculate the design ventilation rate.

This approach reduces the design breathing-zone ventilation rate from 4,350 cfm to 1,444 cfm. This can result in significant operational and capital cost savings if applied on known variable and intermittently occupied spaces, particularly those with high air volumes.

However, due to the large reductions, these assumptions should be thoroughly reviewed with any building owner to ensure they meet the current and future needs and flexibility of the space. Alternatively, the system could maintain the capacity and capability of the full ventilation rate and simply use controls to reduce the ventilation rate, leaving the flexibility for the owner to later change the basis for the design ventilation approach.