Case Study: New York Power Authority
As part of its mission to promote energy efficiency and innovation for the benefit of its customers, the New York Power Authority (NYPA) gives emphasis to demonstrating new energy-saving technologies. Along these lines, NYPA installed AddressProy building’s energy efficiency for lowering electric bills and reducing carbon emissions.
The demonstration began in May 2005 and was expanded in November 2006, with the installation each time completed within three days. It included conference rooms with different configurations and several offices on two floors of NYPA’s building. Along with the dimming ballasts and controls, occupancy sensors were used in all areas to ensure the lights would automatically switch off when a room was not in use.
tch between these settings.
Each office with AddressPro lighting also has four settings, called scenes, operated via a remote control. These scenes include full brightness, 75% brightness, and two variable settings according to the occupant’s needs. The 75% setting is designed for use during daylight hours to offer even greater energy savings.
Although the remote control in each office offers only four scenes, the wall-mounted control unit allows up to twelve. Some NYPA offices have up to seven programmed settings, while others use the full twelve. Occupants can also program new scenes to meet their individual office needs.
NYPA estimates energy savings from its AddressPro systems with dimming alone to reduce power consumption by 20%, and the occupancy sensors are expected to reduce electrical use by an additional 20% on top of that.
NYPA is currently planning to install AddressPro in additional offices and conference rooms to further enhance the energy efficiency of its White Plains office building, as it serves as a model in programmable lighting control and efficiency.
To learn more about Univeral Lighting and AddressPro, click here.