Jekyll Island Convention Center
New construction; Jekyll Island Convention Center; TLC Engineering for Architecture Inc.
Engineering firm: TLC Engineering for Architecture Inc.
2013 MEP Giants rank: 32
Project: Jekyll Island Convention Center
Address: Jekyll Island, Ga., United States
Building type: Restaurant
Project type: New construction
Engineering services: Automation & Controls, Code Compliance, Electrical/Power, Fire & Life Safety, HVAC, Lighting
Project timeline: August 2009 to May 2012
Engineering services budget: $4.39 million
MEP budget: $6.05 million
Being sited on the ocean is a differentiator for the Jekyll Island Convention Center, allowing it to attract business and other meetings to the island and the local economy. Yet that feature posed challenges to the design team. Designing for durability and energy efficiency in a saltwater environment that is also a fragile ecosystem had unique challenges, solved creatively by the closely integrated design team. The owner set a goal of LEED Silver certification, focusing on energy and water efficiency points, to minimize ongoing utility costs.
In order to honor and protect the sensitive ecosystems unique to the coastal environment, the owner targeted LEED NC 2009 Silver certification and addressed that with a water harvesting system consisting of 80,000 gal of rainwater and condensate from 460 tons of cooling capacity being harvested for flushing and irrigation purposes; a solar water heating system; and a 2,500-gal hybrid water heater tank (solar/LP gas) supplying banquet kitchen, laundry, and all back-of-house hot water demand.
Exterior lighting complements the surrounding buildings while highlighting the new convention center. Special attention was given to the fixtures to avoid affecting turtle nesting on the adjacent beachfront. The electrical system, consisting of a 4,000-amp switchboard that feeds multiple distribution, lighting, and appliance panels, was designed to enhance the relaxed beachfront atmosphere. The building's high-efficiency cooling system is supported by two 200-ton nominal chillers. All air handlers use two-way chilled water control valves to match water flow with building cooling demand. Ventilation to the building is through energy recovery units that are varied through demand control. Hot water is provided through a solar-hot water system. LEED NC 2009 Silver certification was achieved in December of 2012, shortly after the convention center opened.
Case Study Database
Get more exposure for your case study by uploading it to the Consulting-Specifying Engineer case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.