Incomplete testing and evaluation of VAV system requires reset
An overhaul of the air handlers at a community college reaped energy savings and improved occupancy comfort.
Through the local electric utility’s energy reduction program, exp US Services was hired to perform retro-commissioning of three of the buildings at a suburban community college. Although the buildings were less than 10 years old, they were not energy efficient and were a source of tenant complaints. The buildings used three large variable air volume (VAV) air handlers with a total fan motor horsepower of 770 hp. The investigation of the HVAC systems revealed that the VAV boxes were never properly commissioned, and the minimum settings were all above the 50% flow setting. Each classroom had a designated VAV box, but because the rooms were often sparsely occupied, these spaces were getting overcooled due to the high airflow. Additionally, the school was paying a double penalty in that the reheat coils in many of the boxes were coming on even in summer, to reheat the overcooled spaces.
Through some minor changes in the building automation system (BAS), the commissioning team was able to reset the VAV flow minimums to much lower settings, and in some cases to zero when occupancy sensors signaled that the room was unoccupied, which was in keeping with the original design intent. The electric energy savings were substantial, and although the engineers did not verify the gas savings, it is estimated they were about 35,000 therms/year.
The facility provided utility data for the before and after periods of September 2009 to August 2010 and March 2011 to February 2012 (see Table 1). This provided an excellent comparison of year-to-year electricity usage and savings.
The Cx team installed amp loggers on an air handling unit (AHU-1), and the before and after data are shown in Figures 1 and 2. It is clear that the new VAV minimum settings allowed the AHU fans to drop to less than 30% of their peak loads, whereas previously the minimum load was never less than about 60% of the peak.
Terrence Malloy is project manager for the energy solutions group at exp US Services Inc. He focuses on energy conservation, retro-commissioning, and renewable energy systems.
Case Study Database
Get more exposure for your case study by uploading it to the Consulting-Specifying Engineer case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.