Fan controls don't measure up
The fan controls at an airport terminal had never been reviewed, and needed to be updated with variable frequency drives.
During a recent inspection of the HVAC systems for a 1-million-sq-ft airport terminal, the exp U.S. Services team noticed the installation of inlet vanes on about 35 of the variable air volume (VAV) air handlers. This seemed particularly odd because the fans were only about 10 years old.
When the engineering team inquired about the installation, the client indicated it was a cost issue and that at the installation time the inlet vanes were a cheaper control method than variable frequency drives (VFDs). It seems that a proper design review by the CxA would have addressed this issue, and perhaps suggested a lifecycle cost analysis (LCCA) to show the actual operating costs of using the inlet vane controls versus VFD controls.
The recommendation: replace the inlet vanes with VFDs. Although a moderately costly option, the annual savings are 2,360,000 kWh and $127,000. As a bonus, the state is offering incentives of about $160,000, so the effective payback is around 3.7 years.
Terrence Malloy is project manager for the energy solutions group at exp US Services Inc. He focuses on energy conservation, retro-commissioning, and renewable energy systems.
Case Study Database
Get more exposure for your case study by uploading it to the Consulting-Specifying Engineer case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.